Prices plus VAT plus shipping costs
Delivery time 30 Workdays
- Order number: E_10998
- Short description: Monitor the level in your fuel, or other liquid storage tanks. Ensure you never run low and are ready for the most critical moments
Tank Depth Pressure Sensors are compatible with all sensorProbe+, securityProbe+ and securityProbe base units. Suitable for any tank up to 20 meters fluid depth. Programmable tank profile provides accurate measurement.
The majority of genset failures are “Failure To Star” error. Much of the time this can be attributed to insuficient fuel. Fuel theft is also a problem for many generators, particularly those at remote site locations which are difficult to monitor and secure. Tank Depth Pressure Sensors can be deployed to tackle many of these comon issues.
- Monitor fuel level and know when to schedule refilling of the tanks
- Monitoring of fuel level for sudden drops that could indicate leakage or theft
- Graphing and record of fuel usage over time
- Compare fuel usage with fuel delivery billing.
Conect to a single sensor port on your sensorProbe+, securityProbe+ or securityprobe base unit. Alerts can be sent through SNMP, E-mail and SMS (with optional cellular data modem). Remote site locations can be monitored from our central monitoring software AKCPro Server, which includes drill down mapping and customizable desktops to display the data you need. sensorProbe+, securityProbe+ and securityProbe devices are Modbus ready, making connection with many generator control panels easy via their Modbus RS485 output. Combined with an Ultrasonic Fuel Level Sensor it gives you a complete remote site generator monitoring solution.
Typical fuel theft is done by inside personel and amounts to just a few litres per day. In a case of one of our African customers 10 litres per day was being skimmed from the tank. Typically this would not be easily detected with fuel level monitoring only. However, witht eh addition of a Modbus connection to the geenrator, it is possible to have a monthly report of total fuel used by the generator and compare this to total fuel used from the tank as read by the TDPS. In this case, 10 litres per day equated to 300 litres per month. The generator flow meter stated 400 litres was consumed, the TDPS showed a drop of 680 litres, showing an obvious large difference in the actual fuel used and the fuel remaining in the tank.
Suspend the TDPS iat the bottom of your tank, and it will sense the pressure exerted by the water column above. Based on the pressure and the type of liqudi you are measuring the depth is calculated. By programming the base unit with your tank dimensions, the total volume in % or litres can be displayed.
TDPS is easy to install, supplied with all mounting hardware required. Simply follow the 5 steps below:
- Measure the total tank height
- Mark the tank height on the TDPS cable and lock cable in that position on the mountaing plate cable gland
- Drill a 30mm Diameter hole for the sensor, and 4x 5mm diameter holes for the mounting plate. Thread the 5mm holes
- Secure the mounting plate in place with the M5 bolts provided
- Seal around the mounting plate with silicone sealant.
|Sensor is calibrated for specific tank size, please select for either max 5, 10, 15 or 20 meter tank when ordering|
|Measurement Method: Hydrolic Pressure(Fluid column pressure)|
|Tank Depth: 0-20 m (65ft) for Water, 0-15m for Petrol, 0-16, 6 m for Diesel|
|Accuracy Distance: 0-2000 cm (65 ft) with 0.2% accuracy for water|
|Full Scale Accuracy +/-0.5% FS (Max)|
|Mounting: Suspended inside the tank vy leader cable|
|Communications Cable: RJ45 jack to UFLS converter box using UTP Cat 5 wire|
|Communications Cable Max. length: 30 meters (100 ft)|
|Ships with a 15 foot CAT6 LAN extension cable|
|CAT6 LAN extension cable be extended up to 30 meters (100 ft)|
|Sensor Part Cable: Leader cable from the sensor part to the converter box is 5/10/15/20 meters respectively based on depth type ordered.|
|Chemical Resistance: Petrol, Diesel, Water|
|Operating Temperature Rate: -20°C to 80°C|
|Protection Grade: IP68 (pressure sensor part)|
|The module operates at 5V from securityProbe5, E-Sensor8 or sensorProbe+|
|The sensor part operates at 12V from an external power supply (provided)|
|Works with certain type of fuel, fres water|
|Requires securityProbe 5E, E-Sensor8 expansion module or sensorProbe+|