Prices plus VAT plus shipping costs
Ready to ship today,
Delivery time appr. 1-3 workdays
- Order number: E_14017
- EAN 0720089658601
- Short description: Smoke Detector - Remote Monitoring of Smoke
Didactum smoke detector - early detection of fire and smoke. The Didactum smoke sensor was developed specifically for the early detection of fire and smoke. The sensor is also compatible with all SNMP enabled Didactum monitoring systems and PDU`s.
Typical applications of Didactum`s Smoke Detector:
- Early warning in case of fire
- Detection of slow burning / smoldering fire
- Fire detection in unmanned, remote infrastructures
- Early detection of ire in enclosures and cabinets
Easy installation of Didactum`s smoke detector
For the early detection of smoke and fire this smoke sensor should be installed on the ceiling of your infrastructures being monitored. You can also easily install this smoke detection sensor in server your cabinets and enclosures. No additional battery is required due to this sensor being powered by the Didactum monitoring base unit.
Simply connect this smoke detector to any one of the analog sensor ports of your Didactum Monitoring System using the patch cable that is included.
Didactum`s built-in auto-sensing feature allows the smoke detector to be automatically listed in the web interface of your base unit. You can then easily set your notifications and alerts in case of fire or smoke. Detector detects smoke indoors. Operating temperature: 0… +70°С. Chain connection is possible. Max. distance of the first sensor from the unit is 150 meters.
(A (smoldering) fire in your server room or data center environment can lead to fatal consequences. By installing suitable smoke detectors catastrophic events can be avoided by being reliably detected and alerted to them at an early stage.)
- Do you have any questions concerning this product?
- Didactum Knowledge Base
- Further products by Didactum
|Technical specifications |
|Maximum distance||150 meters|
|Sensitivity||0,05 — 0,2 db/m|
|Customs code||8531 10 950 1|
|Installation||On the bottom there are mounting holes for fastening smoke sensor to the surface by 4.8×20mm screws or/and bracket and M4 screws.|
|Connection||Detector's jack RJ-12 is connected to an analog input of any system unit using patch-cable RJ-12. Determination of the sensor's type and connection occur automatically. The monitoring system allows to connect several smoke detectors into a linear circuit. For this purpose each detector has two jacks RJ-12: input and output. The first is connected to an analog input of the system unit using a patch-cable RJ-12, the consequent is connected via patch-cable RJ-12 to an output of the first detector and so on. as one sensor with one address.|
|Supply includes||Detector, 4-wired cable RJ11 (2m), 2 screws and 2 nuts M4, 2 screws 4.8×20mm, bracket, double sided sticker.|