Prices plus VAT plus shipping costs
Ready to ship today,
Delivery time appr. 1-3 workdays
- Order number: E_14035
- EAN 0720089658908
- Additional Text: Multi Monitoring - Smoke, humidity and temperature sensor
Smart multi monitoring
Addressable sensor lets you remotely monitor smoke, humidity and temperature in any location in the data center from internet
Embedded temperature sensor
Allows you to measure temperature without additional sensors
Simplifies installation and management by connecting to any other extension units or to master unit directly
Sensor provides 3-level user authentication
Simply connect sensor to any CAN output. Processors - we use NXP
At installation indoors, inside the rack etc., sensor monitors occurrence of smoke, temperature and humidity inside the building. Automatic restoration of power after the actuation. Max. distance from the monitoring unit is 200 meters.
- Do you have any questions concerning this product?
- Didactum Knowledge Base
- Further products by Didactum
|Smoke sensitivity||0,05 — 0,2 db/m|
|Response time||10 sec|
|Accuracy temperature sensor:||±0.4°C in range of -10 °C up 85 °C|
|Operating temperature:||−40°C up +125°С (-40 °F up to 257°F) @ 0 to 100% relative humidity (rH) (non condensing)|
|Accuracy humidity sensor (RH):|| |
± 3% relative humidity (RH) in range of 0 up to 80%
|Maximum distance||200 meters|
|Customs code||8531 10 950 1|
There are mounting holes on the bottom of the case for fastening. Fasten sensor, connect CAN inputs to the input of the previous CAN unit, sensor or of the monitoring unit. The red LED lights up.
|Connection||To connect sensor unit to the system, log into the interface -> Preferences -> Can Config -> CAN1 or CAN2 (depends on which physical port CAN1 or CAN2 of the system the unit is connected). |
Click Config button and wait. The system will poll the bus CAN and give rows with data, if successful will write: Done!. CAN modules and sensors will appear in the list. Click Apply and then click Restart.
Go to --> System Map / Floor Map, click Refresh button, or wait, new devices and new sensors will appear in the tree. Green LED will light up when CAN sensor is connected and successfully determined by the system.
Connection is not successful if after clicking Config, the poll is reset before the phrase "Updating". Check whether terminators on the bus line are set in the right position, change their position using TR switch if needed.
|Supply includes||Sensor, 3-wired shielded patch cable RJ12 (2m), bracket, 2 screws and 2 nuts M4, 2 screws 4.8×20mm, double sided sticker.|
|Net weight||290 g|
Perfect supplementary for server room protection. I'm glad I bought it.
Perfect supplementary for server room protection. I'm glad I bought it. Mark P.